Considerations when connecting Hep2O to a radiator
Hep 2O pipe is compatible with most other makes of fittings, but when connecting it to cylinders and radiators, you should use Hep 2O fittings wherever possible.
The Hep 2O range includes double check valves, tank connectors, gate valves, stopcocks and cylinder connectors. If the use of compression fittings is unavoidable, then check out the jointing instructions outlined on page 24 of our Installer Guide, available to download here.
Things to remember:
- Do not use any jointing compound on the jointing shoulder of the cylinder connector
- Do use PTFE tape
- Don’t use any jointing compound when fitting tank connectors
- Do use sealing washers
Dry lined wall feeds for radiators
There are distinct advantages to using 10mm Hep 2O pipe instead of microbore copper feeds to radiators, one being that Hep 2O pipe can easily be accommodated behind ‘dot and dab’ to give a pipe-free appearance within a room. Unlike copper, it’s not prone to damage such as dents or kinks which can be caused on ‘soft’ copper by other follow-on trades.
How to use our radiator outlet cover plate
A handy solution when using 10mm Hep 2O pipe is to utilise the HX113 Hep2O Radiator Outlet Cover Plate.
Fitted in conjunction with a back box, this cover plate provides a neat, easy-to-install method of connecting radiators. It also has the benefit of a hinged flap that provides an airtight seal.
The box is fixed in a central position behind the radiator with the 10mm pipes dropping out to the radiator valves. This gives a smart professional finish where little or no pipe is seen and, for new build, provides an anchor point for the pipework prior to plastering/boarding as shown below.
Hints for first-fix pipework
- For conventional connections to radiators, the pipe drops should run vertically, side by side at one end of the radiator position
- Where a radiator outlet cover plate is used, the radiator drops should run vertically, side by side, to the centre of the radiator position
- Lateral pipes should be run horizontally through the stud work, avoiding any obvious fixing zones such as skirting boards
- Where subsequent wall fixings are likely, metallic tape should be used to enable an electronic pipe detector to be used
- For fixing pipework to lightweight blockwork, use wooden dowels at each clip position. The HX65 pipe clip is not suitable for fixing directly to such walls because of the low pull-out resistance of the nail.